Recondition my Compabloc heat exchanger
The process of reconditioning a Compabloc heat exchangers involves the steps below. This process ensures your Compabloc welded heat exchanger continues to perform as designed and that the energy losses are minimized over the lifetime of your heat exchanger.
Reconditioning a Compabloc involves the following steps:
- Inspecting the unit for leaks, internal leaks (cross contamination),
- Chemical or heat exchanger mechanical cleaning
- Attaching Alfa Laval factory-certified new gaskets.
- A final hydro testing to the design pressure and making sure the bolts are tightened according to the unit's manual.
Servicing a Compabloc Heat Exchanger
Servicing a Compabloc heat exchanger at one of our Canadian facilities brings your equipment back to its original performance. Using Alfa Laval Reconditioning Services ensures that the equipment performs and is as reliable as the original manufacturer's specifications.
Alfa Laval's workshops are located in Alberta and in Ontario. We recondition, overhaul, rebuild and repair your heat exchanger according to your specific needs, summarizing our activities in a report once the work is completed.
Our state-of-the-art Alfa Laval Service Centres, which use the latest technologies and environmentally sound process, provide the same high quality of service regardless of location.
Let Alfa Laval reduce your maintenance costs over the lifetime of your heat exchangers.
Ten Top Tips To keep your Compabloc in tip top condition
- Ensure that key operating conditions (pressure, temperatures and flow rates) match the original design specifications.
- Use pre-filters and strainers to protect the Compabloc from foreign objects and fouling.
- Open and close valves slowly to avoid water hammer from pressure surges during start-up and shutdown.
- Make sure that the unit is properly vented. For large units the vent connections should be kept opened/connected.
- To ensure stable operation and smooth temperature and pressure ramp up during start up or shut-down, check that the control system complies with the Compabloc manual.
- Use predictive maintenance including regular checks of the pressure drop to determine the cleaning frequency required.
- Use chemical Cleaning-In-Place (CIP) or mechanical cleaning (steam or high pressure water jets) to remove deposits and fouling to avoid having to open the exchanger unnecessarily.
- Panel gaskets must be changed after each panel opening, so keep a spare set of panel gaskets on site.
- After a long shutdown, double-check the tightening torque of all panel bolts before re-starting operation.
- In case of an external leakage, through the gasket, tighten the panel bolts to nominal torque values or replace the panel gaskets. If the leakage cannot be fixed, contact Alfa Laval for advice. Field repair may be possible.
Operation of a Compabloc Heat Exchanger
Contact Service and Parts
24/7 and Field Service
+1 888 253 2226
Alfa Laval Subject Expert: Gina Smith
Field Services Coordinator Ext. 343
Service Centre (Eastern Canada)
Phone: +1 416 299-6101
Fax: +1 416 297-8690
101 Milner Avenue
M1S 4S6, Canada
Service Centre (Western Canada)
Phone: +1 780 413-6349
Fax: +1 780 450-6747
6344 Roper Road
Edmonton, AlbertaT6B 3P9, Canada